Flowchem established a manufacturing unit in 1981 at GIDC Vatva Ahmedabad.
Started manufacturing of process pumps designed in accordance with DIN24256/ISO2858 standard and in general confirming to API 610 and other Industrial pumps with in-house Inspection & Performance witness Testing facility.
Case Study of Flowchem Vertical Cantilever Sump Pump
Customer: Jain Irrigation and Systems Ltd – Jalgaon
Project: Sarigam CETP – Gujarat
Site: Sarigam (Gujarat)
Vertical Cantilever Pumps specialty is that the whole pump is submerged into water and motor at the ground surface.
Flowchem Engineering Pvt Ltd offered Flowchem Vertical Cantilever Sump Pumpset to M/s Jain Irrigation Systems Ltd – Jalgaon through Dealer M/s Maruti Engineers for their upcoming Sarigam Gujarat CETP project.
The tender condition was to pump highly acidic effluent having Ph value: 2 with Solid particle Size up to 100 MM,
Pump Material should be in SS316 with Anti Corrosion coating
Flowchem offered 6.5 Mtr Column length Vertical cantilever Sump pump in All CF8M with Anti-corrosion coating coupled with Kirloskar Electric make 120 HP, TEFC Sq cage induction motor to fulfill tender pump parameter of 700 M3/Hr @ 45 Mtrs Head
Flowchem pumpset offer was technically approved by GIDC and M/s Jain Irrigation technically and call us for commercial negotiation to place Purchase / Work order for 02 Nos Pump-set with some clauses like third party inspection at works and Installation, Commissioning and trial run of said pump set at the site
After long negotiation Flowchem received orders for 02 Nos Vertical Cantilever pumps coupled with 120 HP Motor, Pump to be supplied in ALL CF8M with Anti Corrosion coating on outer and inner parts of the pump.
The motor was outsourced by Flowchem and ordered to procured 120 HP motors from Kirloskar Electric Co Ltd.
Vertical Cantilever pumps were ready and internal inspection was carried after satisfaction, M/s Flowchem raise inspection call to M/s Jain Irrigation Systems Ltd, M/s Jain Irrigation appointed third party M/s Geo Test to inspect pumps at Flowchem Ahmedabad works.
The said pumps were inspected by M/s Geo Test and given their dispatch clearance for dispatch to Sarigam GIDC site.
The said pump set was dispatch through special tempo to site in dismantled condition due to 6.5 mtr column length, The said pumps assembled at the site and 120 HP motor was mounted on Pump motor stool and coupled with coupling; pump set was ready for operation.
Sarigam GIDC representative was to attend the trial run of pump-set at the site, In their presence of GIDC representative visual inspection of pump-set and pump-set trial was taken successfully for 1 Hour and was found satisfactorily as per tender specification, all related Test certificate, Performance Certificate, Material Test Certificate with duty point curve was handed over to M/s Jain Irrigation Systems Ltd
Flowchem Engineering Pvt Ltd
Plot No: 2001, Phase-IV, GIDC, vatva